Please use this identifier to cite or link to this item:
|Title:||Utilisation of Maqalika Reservoir as a source of potable water for Maseru city in Lesotho||Authors:||Letsie, Masupha||Keywords:||Water-supply--Lesotho--Maseru;Municipal water supply--Lesotho--Maseru;Water quality management;Reservoirs--Lesotho--Maseru;Water--Purification;Sedimentation and deposition--Lesotho--Maseru;Reservoir sedimentation--Lesotho--Maseru;Civil engineering--Dissertations, Academic||Issue Date:||2005||Abstract:||Lesotho is a land locked country, entirely surrounded by the Republic of South Africa. Maseru is the capital of Lesotho and the country’s main centre for commerce and industry. The study area is located on the North-Eastern outskirts of the Maseru urban area. The catchment occupies an area of 44km2 with a length of about 13 km and channel slope of 0.4 km/km. The Maqalika Reservoir was built in 1983 to meet the water demands for Maseru city up to 1995, and its storage capacity was 3.7 Mm3. The storage is gradually decreasing as sediment, carried by the natural run-off accumulates in the reservoir. Moreover, water pumped into the reservoir from the Caledon River (which is heavily sedimented) adds its own contribution of silt. The reservoir is located in a very densely populated area, and is heavily polluted leading to high purification costs. The study was motivated by the fact that Welbedacht Dam was constructed in 1973 in the Caledon catchment but downstream of Maqalika. After 20 years, 85% of the volume of the dam was silted. The study was intended in finding whether the positioning of the Maqalika reservoir is acceptable and to find its remaining capacity as a water body supplying a fast growing city. Consideration was also given to the effect of land use practices on the water quality of the Maqalika reservoir, including the cost incurred during purification. The water quality data on physico- chemical was collected from the Water and Sewerage Authority and was analysed using excel spreadsheets. Results obtained were compared with WHO, SABS and National Standards of Lesotho. It was found that nitrates, phosphates and faecal coliforms levels were by far above minimum standards rendering water to be very contaminated and the source being leaking sewers, defeacation in dongas and leachate from Tsosane and Lower Thamae dumping site. Iron levels were also high with mean values beyond 0.3mg/l and the source being leachate from dumping sites, poor disposal of scraps and minerals from soil. Conductivity levels were high and the suspected source is waste solid disposal having a maximum of 442mS/m in March 2001. Hardness, temperature and alkalinity do not pose much danger to Maqalika water since recorded results were almost within limits. Turbidity levels were very high and the main source was found to be catchment sedimentation through run-off. For determination of the impact of sedimentation through pumping, hydrological data was obtained from the Department of Water Affair (DWA) and analysed using Excel spreadsheets to get sediment concentrations. A linear regression graph was plotted using discharge against sediment concentration that yielded y = 0.0007x – 0.0019. This was used in the Rooseboom mathematical equation for estimation of volume occupied by sediment from 1983 - 2002 and was found to be 6789 m3. For determination of the impact due to catchment run-off, a map method of estimating sedimentation from ungauged catchments developed by Rooseboom was used and a volume of 4.598 x 106 m3 was obtained showing that the main contributor of sedimentation in the reservoir is catchment run-off. The chemical costs employed during purification were also compared between WASA and Umgeni Water of Kwazulu- Natal and WASA was found to be expensive with 9 cents/kl while Umgeni spent only 5.24 cents/kl.||Description:||Thesis (M.Tech.:Civil Engineering)-Dept. of Civil Engineering and Surveying, Durban Institute of Technology, 2005 v, 124 leaves, Annexures 1-10, Appendices 1-4||URI:||http://hdl.handle.net/10321/147|
|Appears in Collections:||Theses and dissertations (Engineering and Built Environment)|
Show full item record
Page view(s) 51,684
checked on Jul 18, 2018
checked on Jul 18, 2018
Items in DSpace are protected by copyright, with all rights reserved, unless otherwise indicated.